Install an Arsenic Whole House Water Filter and Make your entire home a healthy place
Concern if your water comes contaminated from a city or a well, instantly transform ordinary water into clean water.
Lead has many useful industrial applications, in water lead, and arsenic is toxic metals and can cause serious cumulative damage to the brain, organs, and blood cells over time. Lead and arsenic occur naturally in groundwaters throughout the world, but most contamination of lead in drinking water comes from lead leaching from service pipes, fixtures, valves, and other materials containing lead, arsenic, and other dangerous metals.
The AdVantEdge™ line of products from AdEdge Water Technologies is a complete line of water treatment products to remove arsenic from drinking water in individual households. The advantage residential water treatment product line includes single tap or point-of-use (POU) systems and whole house or point-of-entry (POE) systems.
Each system uses GFO (granular ferric oxide) adsorptive media that has been proven to be the best for removing both arsenic III and arsenic V in several U.S. EPA demonstration sites, third-party comparison tests, and thousands of successful residential and community water systems across the country.
AdVantEdge™ Medallion Series POE systems are ideal for whole-house arsenic treatment, with no chemicals, no regeneration, and low-maintenance arsenic removal for the entire household. It’s the most economical and effective whole-house treatment available. The adsorption process uses Bayoxide® E33 granular ferric oxide to provide the best arsenic removal performance of any available technology. Medallion Series systems also effectively remove a number of other contaminants.
- Dimensions: 12”W x 52”H Fiberglass
- Quantity of AdEdge Media: 2 Cubic Feet
- Media Type: AD33, or other AdEdgeAD series Media
- Normal Flow Rate: 4-6 GPM
- Peak Flow Rate: 6 GPM
- Backwash Max Flow Rate: 5 GPM
- Backwash Cycles: Automatic
- Inlet/Outlet: 1” dia MPT PVC
- Drain: 1/2” connection
- Under Material: Gravel/stone
- Shipping Weight: 120 lbs
- Temperature Range: 33 F – 100 F
- Arsenic and heavy metal concentration range: 5 – 500 ppb
- Typical treatment goal: < 10 ppb total arsenic
- Arsenic types reduced: As (V) and As (III)
- Removal efficiency: 90-99% typical
- Estimated media life: Water quality and usage dependent
- Spent media disposal: Non-hazardous waste landfill
Recommended incoming water quality for best results:
- pH range: 5.5 – 8.5
- Arsenic: 5 - 100 ppb
- Iron: < 0.5 mg/L
- Manganese: < 0.05 mg/L
- Sulfides: < 0.1 mg/L
- Silica: < 30 mg/L
- Phosphate: < 0.5 mg/L
- Sulfate: < 100 mg/L
- Fluoride: < 1.0 mg/L
- Hardness: < 300 mg/L
The media can operate over a wide range of water quality and utilize no regeneration chemicals, salt, or additives.
Only periodic backwashing is required.
The spent media, upon exhaustion, is easily disposed of as non-hazardous waste.
Arsenic in water can be hard to detect, because it is both odorless and tasteless, and it can be toxic even at low levels.
DESTROY 99.9% of HARMFUL MICROORGANISMS Add Viqua UV Light for Water Disinfection
I have used this system for 2 years and am extremely satisfied
I like tap-cold water better than fridge-cold water. I also like filtered water for tea and coffee. My only reasonable option before was a filtered pitcher.
We purchased our new, last, forever home recently and we loved everything about it, except the water smelled horrible. We have always preferred well water, but we didn't remember the water smelling this bad when we inspected the home prior to closing. We tried the activated charcoal shower head filters, but they did very little, if anything and I was beginning to think this was never going to be mitigated. We looked at every method out there and this system looked like the best option, if it would work. The filter changing method is by far the best available, so we settled on the Aqua-Pure. I installed it with CPVC and added added a spin down sediment filter in front. It took about 3 hours to plumb. After finishing late that evening, we checked the shower for smell and it was still there, but not as bad. By the next day it was completely gone and has been that way since. We had to cycle all of the old water out of the water heater before the smell would subside. We have had clean, odor free water for a month now and I can't say enough good things about this product. We'll see how long the filter lasts, but I'm hopefully optimistic that we can get 6 months to a year before a change. Great price, great system, simple solution.
We recently moved to a home with a city water supply after more than 10 years of mountain fresh well water. I just wanted something inexpensive that would remove the chlorine taste. Not thrilled with the thought of attaching a bulbous knob on the end of the sink nor a separate tap which most kitchen sink filters require, I took a chance on the Waterdrop 10UA. The fact it plumbs into the existing cold water side of the faucet was especially appealing as it is both a cleaner look and a much easier installation.
I live in Florida and our water had that Florida water taste Long with chlorine. After installing this filter, the water is very nice!